Avcon Controls offers Air Gas Ratio Regulators, Type GG/GGB/GGO.
Safety Solenoid Valve must always be fitted upstream of Air Gas Ratio Regulator and in the direction of flow marked on the valve body. The spring retaining dome must be installed downwards. Spring force of GG can be adjusted by means of a 6 mm Allen key. During installation of GG/GGB, fixed orifice plates or variable flow resistor must be used in the gas line as well as combustion air pipeline. These orifice plates will determine and fix Air Gas ratio required for complete combustion. When using GGO, variable flow resistor / orifice plate should be provided in the gas pipe line, before mixture (Injector). If combustion air pressure is higher than the gas inlet pressure, the variable flow resistor should be used to turn down the gas control pressure.
ASAPP INFO GLOBAL SERVICES PVT. LTD A-303, Navbharat Estate, Zakaria bunder Road, Sewri(West), Mumbai-400 015, Maharashtra, India.
© IPFOnline 2020 All Rights Reserved.